Incorrect use of the positioner Type and Type can be dangerous to people, Bürkert. In view of the wide range of possible application cases, check . ,.nearby. environment.. The device is designed to be mounted on. Buy Now, In Stock: Burkert , Type Digital Electropneumatic Positioner for Integrated Mounting on Process Control Valves.
|Published (Last):||1 January 2011|
|PDF File Size:||7.11 Mb|
|ePub File Size:||1.98 Mb|
|Price:||Free* [*Free Regsitration Required]|
Page 2 We reserve the right to make technical changes without notice. LIMIT menu, the mechanical end position monitor has only limited relevance. Transfer Of Several Process Values For selecting the correct burkerf please refer to the technical data, images and notes for proper use according to the data sheet.
The actuator burkedt from its rest position to the end position. Vurkert key After reaching the last decimal place, the display switches back to the first decimal place. USER — Calibration of actual value and set-point value The following values can be manually calibrated with this function: Page TypeAuxiliary functions If several diagnosis messages are available with different status signals, the status signal with the highest priority is shown on the display.
The display is adjusted to the set functions and operating levels. Can be combined with.
Burkert 8692 Operating Instructions Manual
Electropneumatic positioner and process controller. TypeAdditional technical information Adjustment. PCONact can be selected for Type burkfrt controller only.
TypeAuxiliary functions If several diagnosis messages are available with different status signals, the status signal with the highest priority is shown on the display.
CHECK; end position monitor. The input screen is opened. Page 34 TypeInstallation Thank you for visiting www. INP 20mA 0 calibr.
MODE Value range 0, 1 or Can be combined with. During the installation, the collets of the pilot air ports must not be fitted to the actuator. Example 2 Of A Process Controller type Pneumatically operated 2 way angle seat Specify which functions are to be executed when X.
Don’t have an account? Page Page Page – Configuration. A progress bar on the display indicates the position of the actuator and the speed of aeration and deaeration. As a result, the 4 — 20 mA standard signal fails. MIN Open bukrert setting for lower temperature limit.
Page 48 TypeInstallation Move the actuator back to the rest position Turn the hand lever to the left with a screwdriver. We reserve the right to make technical changes without notice.
BURKERT OPERATING INSTRUCTIONS MANUAL Pdf Download.
CMD – Sense of effective direction o The auxiliary function is activated via the ADD. Transfer of set-point and actual value Page – Table. For special requirements the X.
The device incorporates the main function groups – Position sensor – Electro-pneumatic control system – Microprocessor electronics The position sensor measures the current positions of the continuous valve.
The control of single or double-acting actuators is done without internal air consumption. For selecting the correct product please refer to burkrt technical data, images and notes for proper use according to the data sheet.
Designs TypeDescription of System 5. Type Pneumatically operated 2 way Globe Control Position control circuit in Type english Position of the decimal point of the process actual value.
Burkert Type 8692 Electro Pneumatic Positioner
Page 70 TypeOperation Possible. The buekert of the current position POS or of the set-point value CMD can be transmitted to the control center via the analog output.
TypeAuxiliary functions ADD.